Installation Manual for Buderus G115 Direct Vent Oil Boilers
View original pdf
to seal all flue joints and screw penetrations to prevent leakage of flue gases into the building. Pipe joints and other possible flue gas leakpaths should be sealed with
high temperature silicone
F rated silicone
, GE. 106 or equivalent, or high temperature tape (360
F rated aluminum foil tape
VentureTape CW or equivalent) as necessary. The venting
system shall not be pierced
under any circumstance after initial installation.
Combustion measurements shall be performed at the exhaust termination and/or overfire. The breeching can be pierced for testing as long as the hole
is sealed airtight with a bolt
, washers and high temperature silicone.
Separate air intake hood and aerocowl exhaust termination
Advise owner to keep intake and exhaust terminations free of debris and snow.
G115/21 riello bf
files -> Home: unexpected inconsistency; run fsck manually.
files -> BfmuserManual40 60lbs indd
files -> User’s manual sitGo™ Collapsible Rear Leg Support Dog Wheelchair
files -> Rrocurement of
files -> Manual for Procurement of Goods Cover
files -> Timed up & Go Test 6 Minute Walk Test
Share with your friends:
The database is protected by copyright ©userg.info 2017