1. Oil pump pressure should be 140 - 150 psi for the Riello BF burners 140 - 150 psi for the Carlin P burners. Make adjustments if necessary. 2. Adjust the air set to get a CO value of 11.0% – 12.5% with 0 smoke #. Perform final test with all covers and inlet piping in place. NOTE:Stop burner operation at once if smoke emerges from the exhaust terminal. Check and make necessary burner adjustments to obtain smoke-free flue products. NOTE: MAKE SURE the burner observation port located on the burner door is sealed airtight by properly tightening the port screw. Use extra sealant if necessary. NOTE: Affix the transparent blank cover label over the boiler rating plate. Affix the electrical and clearance label on the boiler jacket near the boiler rating plate.
10 The boiler and vent system should be inspected and serviced once annually by a qualified service person to maintain efficient operation of the system. Proper operation of boiler controls and safety devices must be verified during the annual service. Maintenance and service procedures